The Uni3 Main Building is the multitenant facility of the campus where we have office spaces and co-working areas alongside our state of the art conference and event center. This is also where you find our restaurants, snack bars, flower shop and other services.
Vending machines providing beverages, food and snacks can be found on floor 1.
Fire protection and fire alarms
Click here to see which area you are located in Uni3 Main building.
This part consists of 14 floors, floor 0 (basement) and the Theatre.
The system in this part operates in the exact same way as the system in Area DE when it comes to how the fire and evacuation alarm is triggered on the separate floors.
The difference is the Theatre where there are both sirens and a spoken fire and evacuation alarm.
Floor 1: When detectors on floor 1 are triggered it only activates the evacuation alarm on floor 1 and the spoken evacuation alarm on floor 1 & 2 and within the Theatre.
Floor 2: When detectors on floor 2 are triggered it activates the evacuation alarm on floor 1 & 2 and the spoken evacuation alarm on floor 1 & 2 and within the Theatre.
The Theatre: When detectors in the Theatre are triggered it activates the evacuation alarm on floor 1 to 6, and the spoken evacuation alarm on floor 1 & 2 and within the Theatre.
If you should hear an evacuation siren or a spoken evacuation message, even if it is not on your direct floor. You should evacuate in a calm and orderly fashion and make your way to the assembly point.
This part of building consists of 8 floors and floor 0 (basement), and the alarm triggers as follows:
Floor 0: When 1 or more detectors on basement level are triggered, the evacuation alarm will sound.
Floor 0,5–1,5: When 1 or more detectors on floor 0,5–1,5 are triggered, the evacuation alarm will sound. It will also sound if at least 2 detectors on floor 0 are triggered. In addition to the alarm sound there is also a spoken (voice) evacuation alarm, this voice tells you to evacuate both in Swedish and English. The spoken alarm is only available on floor 0,5–1,5.
Floor 2: When 1 or more detectors on floor 2 are triggered, the evacuation alarm will sound.
Floor 3–8: When 1 or more detectors on the floor are triggered, the evacuation alarm will sound. It will also sound if at least 2 detectors on the floor below are triggered.
The assembly point is located at Hugo Hammars quay.
1 first aid kit by the toilet/shower close to stairwell E
1 defibrillator across from Uni3 Front Desk by the exit
1 defibrillator in Uni3 Conference Centre across elevator stairwell E
2 first aid kit by the toilets in Uni3 Conference Centre by stairwell D
2 first aid kit by the toilets in Uni3 Conference Centre by stairwell E
Climate curtains at different areas behavior slightly different.
In area D & E on each floor (see area here) there is a keypad for manually overriding the automated function. There are also local control panels in meeting rooms and open landscapes where windows are equipped with automatic climate curtains.
Lights in house are controlled via a KNX bus system with a presence sensor, time control, and local light switches.
A motion detector activates lights during movement in most public areas. In the daytime, the lights are in a passive state in the absence of movement and low lighting on the walls and ceilings are off. In the evening, the lights are off completely in the absence of movement.
There are local switches in many conference rooms. Click “Belysning +” to turn them on, and long press the button to adjust the light until satisfied. Don’t forget to turn them off when you leave by pressing “Belysning –“.